Our best varistors power frequency voltage, D30 High Performance MOVSd, Low Voltage Distribution Arrester has been well-received by our customers due to its high quality and competitive prices. Since the establishment of our company, we are constantly increasing the pace of integration and our business continues to grow at a high speed. We pursue the goal of sustainable development and build it on the basis of customer satisfaction. Through the continuous pursuit of quality and technology, we have a one-stop production process and become a company trusted by domestic and foreign partners. On the basis of honesty and trustworthiness, we have been considering how to meet customer needs, and have strengthened quality and product power with variety.
|suggested rated voltage (kV)||3.2||4.9||5.4|
|DC U1mA (kV)||4.85±0.3||7.3±0.45||8.1±0.5|
|IL at 75% of U1mA (µA)||≤ 15||≤ 15||≤ 15|
|typical Ures / U1mA||1.81||1.81||1.81|
|repetitive charge transfer Qrs (C)||0.5||0.5||0.5|
|guaranted 2ms test current (A)||350||350||350|
|max 2ms test current (A)||400||400||400|
|4/10µs high current test (kA)||100||100||100|
|nominal discharge current In (kA)||10||10||10|
|accelerated ageing test||115℃|
Kct ≤ 1.0
Kct ≤ 1.0
Kct ≤ 1.0
Our goal is to produce and operate mainly Thunder Arrester Polymeric Composite Lightning Arrester Fuan Resistors and develop related service in synergy with each other. Thanks to the enthusiasm and wisdom of all our employees, we have made great progress in product quality, service and after-sales. Our company always adheres to the tenet of 'quality is life, users are God', providing customers with high-quality products and services, and advancing side by side with customers.
Hot Tags: d36mm metal oxide blocks for distribution arrester China, suppliers, manufacturer, factory, distribution class, high voltage, high performance, medium voltage, test, size, best, IEC 60099-4 2014, distribution networks, surge protection, metal oxide varistor specifications, metal oxide resistors, D30 High Performance MOVSd, railway surge arresters, metal oxide varistors test