Our company has a managerial team with unity, high efficiency and strong implementation power. With the tenet 'honest, being professional, quality, high efficiency', we provide customers with perfect solution of high gradient varistors size, polymer-housed surge arresters test, lightning protection. Warmly welcome to visit our factory. And because Kayo deals in the entire spectrum of protective equipment, our customers don't have to waste time shopping around. We look forward to getting your inquiries. We will uphold the business philosophy of 'brand management, quality win, people-oriented, harmonious development', accelerate the pace of technological innovation, and optimize the product structure. We sincerely cooperate with domestic and foreign customers and all sectors of society to create a better future! Our products will continue to enhance within the order and look forward to cooperation with you.
|suggested rated voltage (kV)||3.2||4.9||5.4|
|DC U1mA (kV)||4.85±0.3||7.3±0.45||8.1±0.5|
|IL at 75% of U1mA (µA)||≤ 15||≤ 15||≤ 15|
|typical Ures / U1mA||1.81||1.81||1.81|
|repetitive charge transfer Qrs (C)||0.5||0.5||0.5|
|guaranted 2ms test current (A)||350||350||350|
|max 2ms test current (A)||400||400||400|
|4/10µs high current test (kA)||100||100||100|
|nominal discharge current In (kA)||10||10||10|
|accelerated ageing test||115℃|
Kct ≤ 1.0
Kct ≤ 1.0
Kct ≤ 1.0
In an ever-changing marketplace, we continue to make new advances every year by offering the best 10d201K 10d390K 10d431K 10d471K Zov Zinc Oxide Varistor to people. We can provide customers with advanced and reliable products and 'professional, timely, efficient, and high-quality' intimate services, allowing you to take the lead in the ever-changing market. We are sincerely welcome good friends from numerous circles at dwelling and abroad come to cooperate!
Hot Tags: d36mm metal oxide blocks for distribution arrester China, suppliers, manufacturer, factory, distribution class, high voltage, high performance, medium voltage, test, size, best, IEC 60099-4 2014, distribution networks, metal oxide varistor testing pdf, D28H23.5 metal oxide varistorsd, polymer-housed surge arresters test, D28 High performance AC metal oxide varistors size, Metal Oxide Varistors For DC Arresters, porcelain surge arrester size